We look forward to providing you with the finest quality products and services available.
Emergency / Toll-Free:
Local: (954) 785-7800
Paper Fax: (954) 785-7804
E-Fax: (954) 208-0101
3000 Gateway Drive
Pompano Beach, FL 33069
Please fill out the form provided below. We will get in contact with you as soon as possible.
Would you like to request a quote for a Bass United Systems, Inc.?
Fire Alarm Systems and Elevator Recall
What is elevator recall and why is it necessary?
Elevator Recall is the operation of an elevator when it is recalled to a specific landing and removed from normal service because of activation of firefighters’ service, either automatically or manually. In the event of a fire alarm activation or stand-alone elevator recall initiating devices (smoke and heat detectors), from a device located in elevator lobbies, elevator machine room, or elevator shaft, the cabs are automatically recalled to a facility’s predetermined floor of egress, and illuminates a fireman’s hat or flashing hat, should the smoke detector in the elevator shaft or machine room activates. This alerts the firefighters that are using the cab that fire may be present in the elevator shaft or machine room, making the use of the elevator a risk to their safety. Elevator recall is automatically or manually initiated to prevent the possibility of the public being delivered to a smoke or flamed-filled area. The cab will proceed immediately to the proper level and open its doors.
In buildings with fire sprinklers located in an elevator machine room and elevator shaft, a placement of a heat detector within 24 inches of the sprinkler head, and connected to a fire alarm system shall cause a shutdown to the elevator power via a shunt trip mechanism when activated. The purpose is to save the equipment from electrical damage, wet breaks, or an uncontrolled loss of power which may cause individuals being trapped with possible deadly results.
The requirement for fire alarm systems and elevator recall is referenced through numerous codes, as addressed by ASME A17.1, ASME A17.3, NFPA 13, NFPA 70, NFPA 72, NFPA 101, local building code or local building ordinance. Enforcement by both the fire department (AHJ) and the local elevator inspection department may be required. This research can get complicated to due to each code addressing a slice of the pie, so there isn’t one location that you could look to for application guidance. We strongly recommend you hire a local professional (fire alarm contractor, electric contractor, elevator contractor or engineer) to help you through this complicated process.
Here are other code requirements to consider as well:
In summary, the fireman’s elevator recall and fire alarm system may need to meet additional criteria that apply to less than common circumstances, so be sure to employ an experienced fire alarm contractor that will proactively coordinate the electrical and elevator interfacing requirements. A properly coordinated integration between the two systems can make the difference between passing the first inspection and incurring additional costs due to subsequent re-inspections.
Feel free to call us today for your free fire alarm and elevator recall evaluation - 1-800-372-2770